CALCULATION FACTOR POWER WITH USING BANK CAPACITORS ON LOAD INDUSTRY
In an electric power system there are three types of power, namely active power, apparent power and power reactive. Some industrial loads such as induction motors operate at a power factor quite low. If this problem is not solved it will cause power loss and drop voltage. Wrong one method resolve problem the that is with adding a capacitor bank as a reactive power compensator. On the installation of capacitors with the power factor increased from 85%, the capacitor rating results are 321 kVAR and on moment raised 90% obtained results rating capacitor 428 kVAR and on moment raised 95% obtained results rating capacitor 553 kvar.